P91 is a Creep Resistant Steel – Weld Performance is Dependent on Chemical Composition
We performed an assessment of metallurgy and welding procedures for attaching appendages to P91 heavy wall pipe.
Failures in times as short as 1500 hours after start up were found in a power plant. The cause was found to be related to the original P91 supplier – including hot forming, and improper post weld heat treatment. Appendages such as lifting lugs and alignment fixtures are welded to heavy wall pipe to facilitate installation of piping in a power plant. After these appendages have served their purpose, they are removed. These appendages are generally located adjacent to circumferential welds that are subjected to post weld heat treatment (PWHT) as required for the P91 steel.
P911 is a specially modified and heat treated steel that performs quite well at elevated temperature – usually 1,000 F and higher. Since it is a highly hardenable alloy, it’s subject to hydrogen cracking. The performance of Grade 91 welds depends entirely on having the correct chemical analysis in the weld metal. Welding of P-91 CSEF pipe must be done with strict adherence to welding procedures and post heating schedules in order to attain a satisfactory microstructure in the weld and base metal.
P91 is a creep resistant martensitic steel used extensively in the generation of electric power. It is nominally a 9%Cr-1%Mo-I/4%V plus other small additions. The martensite structure is developed by heating the steel to a high temperature (austenitizing temperature) and then rapidly cooling to a temperature where the austenite transforms to martensite; the second step tempers the martensite to soften the microstructure.
The optimum properties for P91 steels are achieved in the quenched and tempered condition. To achieve the fully martensitic structure in weldments, the steel must be cooled to a temperature where the entire parent structure, austenite, has transformed.
This martensite finish temperature is about 200 F. In addition, the interpass temperature must be kept below about 600 F to prevent the austenite from being stabilized. This is a condition that prevents full transformation to martensite. Because martensite formed during welding is very hard and prone to cracking, the weldment must be subjected to a PWHT following any welding.
The PWHT provides tempering of the newly formed martensite. Another characteristic of P91 is that it’s prone to hydrogen induced cracking. Prevention of this cracking requires high preheat temperatures. The combination of high preheat temperatures and a low interpass temperatures makes the weldability “window” small. It’s important to recognize that P91 is designed and processed to optimize creep and creep-rupture strength.
The quality of the welding process is through the implementation of precise and controlled welding procedures that assure that these practices are carried out.
We Perform Weld Troubleshooting/ Consulting on Various Types of Equipment for Clients in Industries including Energy, Mining and Petrochemical.
– Failure Analysis on Cracked Tube to Tubesheet Welds on Chemical Reactor
– Failure Analysis of Premature Weld Cracking in Stainless Steel Exhaust Ductwork
– Weld Repair of Mis-Machined Cast Turbine Blades